PO Box 44480
Olympia WA 98504-4480
Phone (360) 902-6130
Fax (360) 902-6132
METRO TRANSIT DIVISION
DEPARTMENT OF TRANSPORTATION
201 S JACKSON ST MS/KSC-TR0828
SEATTLE, WA USA
METRO TRANSIT DIVISION
UNIVERSITY STREET STATION
SEATTLE, WA 98101
Permit Expiration Date:
Dear Building Owner:
During a recent inspection of the conveyance listed above, an inspector for the Department of Labor & Industries found conditions that must be corrected to ensure safety and compliance with applicable codes. The enclosed inspection report will tell you what must be corrected. The building owner is responsible, under RCW 70.87.120, for ensuring that all corrections are made. If you are unsure which corrections must be made by a licensed elevator mechanic please contact your elevator service company for assistance. Please note, you should provide your elevator service company with a copy of this inspection report for their information as we do not provide them with a copy.
To protect the safety of those who use your building, and to avoid substantial penalties required by law (RCW 70.87.185 and WAC 296-96-01070), and to prevent us from removing your elevator from service (RCW 70.87.125)
YOU MUST RETURN THIS COMPLETED REPORT BY THE DUE DATE.
Once the corrections have been completed, check each one off using the checkboxes provided; sign and date the report; and email, mail or fax to the address or fax number listed above
by the due date.
You may call us at (360) 902-6130 for more information. You may also find a copy of this inspection report online at
Thank you for giving this safety issue your prompt attention.
THIS CONVEYANCE HAS BEEN INSPECTED AND THE FOLLOWING DISCREPANCIES WERE NOTED AND SHALL BE CORRECTED WITHIN 90 DAYS. WHEN CORRECTIONS ARE COMPLETED PLEASE INDICATE IN THE BOX PROVIDED NEXT TO EACH DISCREPANCY THAT IT HAS BEEN COMPLETED. UPON COMPLETION OF ALL CORRECTIONS, OWNER, PLEASE DATE AND SIGN BELOW AND RETURN A COPY OF THIS REPORT TO OUR OFFICE BY THE DUE DATE.
A17.1-805.1b(1) Make stop switch cover buzzer operational. 80dBA minimum sound level required. Repair bottom stop switch cover.
A17.1-805.1k Make all demarcation lights operational.
A17.1-802.6a Replace all broken combteeth.
188.8.131.52.1 Maintenance records shall document compliance with 8.6 of the Code and shall include records on the following activities (a) description of maintenance task performed and dates Owner you have no records of the activities listed above.
Maintenance records shall have conveyance numbers on them. Maintenance records not up to date.
8.6.8 The maintenance of escalators shall conform to 8.6.1 through 8.6.3 and 8.6.8. 184.108.40.206 Handrails. 220.127.116.11 Step-to-Skirt Clearance. Due January 1,2010 18.104.22.168 Step/Skirt Performance Index. Due January 1,2010 22.214.171.124 Combplates 126.96.36.199 Escalator Skirt Panels. 188.8.131.52 Steps 184.108.40.206 Rollers, Tracks, and Chains. 220.127.116.11 Signs. 18.104.22.168 Guards at Ceiling Intersections. 22.214.171.124 Antislide Devices. 126.96.36.199 Handrail Guards. 188.8.131.52 Brakes. 184.108.40.206 Cleaning. 220.127.116.11 Entrance and Egress Ends. Owner one or all items is not addressed with your Maintenance control program. Some items may not be inclusive to your escalator. Inspectors note the missing items.
Perform step/skirt index performance test and provide documentation on site.
The data plate shall indicate the Code in effect at the time of installation. The data plate shall also indicate the Code in effect at the time of any alteration and indicate the applicable requirements of 8.7. The data plate shall be in plain view and securely attached to the main line disconnect or on the controller. The data plate material and construction must have letters and figures stamped, etched, cast, or otherwise applied to the face and must remain permanently and readily legible. The height of the letters and figures shall be not less than 0.125 inches. See A17.1d–2000 and earlier editions — 215 A17.1–2000 and later editions — 8.9 and 18.104.22.168 WAC 296-96-00650 (code in effect). Inspectors note discrepancies to the code data plate and indicate the installation date or any alteration performed after 7/1/2004
Install code year data plate and /or alteration data plate on exterior of unit.